# High Speed Fuses - Cooper Bussmann

and the correction factor. X. Arc Voltage. This curve gives the peak arc voltage, UL, which may appear across the fuse during its operation as a function.

High Speed Fuses Section Contents Page General Applications . . . . . . . . . . . . . . . . . . . . . . . . 94-95 North American fuses & accessories . . . . . . . . . . . .94-113 DFJ - High speed Class J fuse . . . . . . . . . . . . . . . . . . .97 Square Body fuses & accessories . . . . . . . . . . . . 114-176 BS 88 fuses & accessories . . . . . . . . . . . . . . . . . .177-185 Ferrule fuses & accessories. . . . . . . . . . . . . . . . . .186-206

High Speed Fuses

93

High Speed Fuses

General Applications Rated Voltage

Power Factor

The AC voltage rating of Cooper Bussmann® fuses is given in volts rms. Fuses tested to IEC are tested at 5% above their rated voltage. British Style BS 88 fuses are tested at 10% above its rated voltage. UL recognition tests are performed at the rated voltage.

For other power factor values, the total clearing integral can be calculated as a multiple of the clearing integrals, the correction factor K and the correction factor X.

1.0

Arc Voltage

0.7

Rated Current Rated current is given in amps rms. Cooper Bussmann fuses can continuously carry the rated current.

X

0.9

0.8

Melting Characteristic The melting 10 6 4 characteristic 2 shows the virtual 10 melting time in 6 4 seconds as a 2 function of the 10 6 prospective current 4 in amperes rms. 2 10 The fuses are 6 4 specially 2 constructed for 10 6 short-circuit 4 protection against 2 high level fault 10 6 currents. Loading 4 2 and operation of 10 the fuse in 6 4 the non2 continuous/dashed 10 6 section of the melt 4 curve must be 2 10 avoided. The curve 2 4 6 8 10 2 4 6 8 10 10 Prospective Current In Amperes RMS can also be read as the real melting time as a function of the RMS value of the pre-arc current. 4

3

1

0

–1

–2

–3

–4

1

2

Clearing Integrals

1.5

The total clearing I2t at rated voltage and at power factor of 15% are given in the electrical characteristics. For other voltages, the clearing I2t is found by multiplying by correction factor, K, given as a function of applied working voltage, Eg, (rms).

1.0

3

K

0.2

0.3

0.4

103 9 8 7 6 5 4 Eg 200 300

Watts loss at rated current is given in the electrical characteristics. The curve allows the calculation of the power losses at load currents lower than the rated current. The correction factor, K p , is given as a function of the RMS load current, Ib , in % of the rated current .

0.5 COS ␸

1.4 1.2 UL

3

Power Losses

400

500

600 660

1.0 Kp 0.8 0.6 0.5 0.4 0.3 0.2

Ib

0.1 30 40 50

60

70

80 90 100%

Cut-Off Current A fuse operation relating to short-circuits only. When a fuse operates in its current-limiting range, it will clear a shortcircuit in less than 1⁄2 cycle. Also, it will limit the instantaneous

0.5 0.4

105

0.3 0.2 Eg 100 200 300 400 500 600 660

Peak Let-Through Current

Virtual Pre-Arcing Time In Seconds

2

0.1

This curve gives the peak arc voltage, U L , which may appear across the fuse during its operation as a function of the applied working voltage, E g , (rms) at a power factor of 15%.

104

103

A B

2 ≈ 10 2 102

103

104 Prospective Current in Amps RMS

105

106

peak let-through current to a value substantially less than that obtainable in the same circuit if that fuse were replaced

94

For product data sheets, visit www.cooperbussmann.com/datasheets/ulcsa

High Speed Fuses

General Applications with a solid conductor of equal impedance. A asymmetrical current B symmetrical current Parallel Connection When fuses are connected in parallel it is recommended that the applied voltage does not exceed 0.9 UN (the rated voltage of the fuse). This is due to the fact that the energy released within the fuses may be unevenly shared between the parallel connected barrels. When fuses are connected in parallel, one must take into account that the current sharing is not necessarily equal. And it must be checked, that the maximum load current is not exceeded.

Fuses in series may not equally divide the applied voltage. It is recommended that series connected fuses should only be operated at fault currents that yield melting times less than 10 ms and a recovery voltage per fuse of less than or equal to 0.9 UN (the rated voltage of the fuse). Mounting Guidance The recommendations below have to be followed when mounting a Cooper Bussmann fuse with end plate threaded holes. 1. Screw in studs: 5 N•m Max, 3 N•m Min 2. Attachment of the fuse to bussbar by means of nut and washer: Thread Configuration 5 ⁄16” – 18, M8 3 ⁄8” – 16, M10 3 ⁄8” – 24 1 ⁄2” – 13, M12 1 ⁄2” – 20 *1 N•m = 0.7375 lb-ft

Torque (N•m)* Max Min 25 20 45 40 45 40 65 50 65 50

Overloads The design of Cooper Bussmann® fuses is such that they can be operated under rather severe operating conditions imposed by overloads (any load current in excess of the maximum permissible load current). In applications, there will be a maximum overload current, Imax, which can be imposed on the fuse with a corresponding duration and frequency of occurrence. Time durations fall into two categories: 1. Overloads longer than one second 2. Overloads less than one second termed “impulse” loads. The following table gives general application guidelines which, in the expression Imax < (% factor) x It. It is the

Frequency of Occurrence Less than once per month Less than twice per week

Overloads (> 1 sec) Imax < 80% x It Imax < 70% x It

Impulse Loads (< 1 sec) Imax < 70% x It Imax < 60% x It

Several times per day

Imax < 60% x It

When impulse loads are an intrinsic/normal parameter of the load current either as single pulse or in trains of pulses or when their level is higher than the melting current at 0.01 seconds (per time-current curve), contact Cooper Bussmann for application assistance. In addition to the parameters set forth in the preceding table, the RMS value of the load current as calculated for any period of 10 minutes or more should not exceed the maximum permissible load current. Furthermore, it is important that a fuse should not be applied in the non-continuous/dashed portion of the associated time-current curve. Any time-current combination point which falls in the non-continuous/dashed portion of the time-current curve is beyond the capability of the fuse to operate properly. DC Operation Depending upon the short-circuit time constant and the magnitude of the prospective short-circuit current, the dc voltage at which a fuse can be applied may be less than its ac rating. Long time constants require a lower dc voltage. Conversely, however, higher available prospective shortcircuit currents result in faster fuse openings and thus permit a fuse to be operated at a higher DC voltage. Consult Cooper Bussmann for additional information and application assistance when fuses have to operate under DC conditions.

1.0

0.8

Reduction Factor

0.9

Conductor Cross Section

0.5 0 .6 0.7 0 .8 0.9 ≈ (IEC cross section)

1 .0

Reduction of permissible load current when the conductor cross section is less than that given in IEC Publication 269-1 & 4 valid for Cooper Bussmann high speed fuses. Application Assistance If you have application problems or need a fuse outside our standard program, please contact the nearest Cooper Bussmann representative. Phone numbers are shown on the back cover.

For product data sheets, visit www.cooperbussmann.com/datasheets/ulcsa

95

High Speed Fuses

Series Connection

melting current corresponding to the time “t” of the overload duration as read from the time-current curve of the fuse. The guidelines in the table below determine the acceptability of the selected fuses for a given Imax.

High Speed Fuses

North American Fuses

Introduction General Information

North American Contents Catalog Number DFJ FWA FWA FWX FWH KAC KBC FWP FWJ

Amp Range 1-600 1000-4000 70-1000 35-2500 35-1600 1-1000 35-800 5-1200 35-2000

Volts 600 130 150 250 500 600 600 700 1000

Accessories Fuse Bases

113

North American Fuse Ranges Amps 1000-4000 70-1000 35-2500 35-1600 1-1000 5-1200 40-600 35-2000

96

Page 97 98-99 100-101 102-103 104-105 106 107 108-110 111-112

Volts 130 150 250 500 600 700 800 1000

AC X X X X X X — X

DC X X X X — X X —

Cooper Bussmann offers a complete range of North American blade and flush-end style fuses and accessories. Their design and construction were optimized to provide: • Low energy let-through (I2t) • Low watts loss • Superior cycling capability • Low arc voltage • Excellent DC performance North American style fuses provide an excellent solution for medium power applications. While there are currently no published standards for these fuses, the industry has standardized on mounting centers that accept Cooper Bussmann fuses. Voltage Rating All Cooper Bussmann® North American style fuses are tested at their rated voltage. Cooper Bussmann should be consulted for applications exceeding those values. Accessories External and internal open fuse indication is available for selected portions of the North American line. Fuse blocks are available for most applications.

For product data sheets, visit www.cooperbussmann.com/datasheets/ulcsa

High Speed Fuses

Drive Fuse High Speed Fuses Time-Current Characteristic Curves—Average Melt

Specifications Description: High speed, current-limiting fuse. The Cooper Bussmann® Drive Fuse will provide maximum protection for AC and DC drives and controllers and meet NEC® branch circuit protection requirements. The Drive Fuse has the lowest I2t of any branch circuit fuse to protect power semiconductor devices that utilize diodes, GTOs, SCRs and SSRs. Dimensions: See page 15 for Class J dimensions. Construction: Melamine tube with silver fuse element. Ratings: Volts — 600Vac (or less), 450Vdc (or less) Amps — 1-600A IR — 200kA RMS Sym., 100kA DC Agency Information: CE, Std. 248-8, Class J, UL Listed, Guide JDDZ, File E4273, CSA Certified, Class 1422-02, File 53787.

Current Limitation Curves

High Speed Fuses

DFJ Class J

Features and Benefits • Easily coordinated with existing and new variable speed drives and electric controllers. • Standard Class J dimensions allowing the use of readily available fuse blocks, holders, and switches. • Allows the lowest let-thru energy of any branch circuit overcurrent protective device. Typical Applications • Protection of ac & dc drives • Equipment using power semi-conductor devices Catalog Numbers (Amps) DFJ-1 DFJ-2 DFJ-3 DFJ-4 DFJ-5 DFJ-6 DFJ-8 DFJ-10 DFJ-12

DFJ-15 DFJ-20 DFJ-25 DFJ-30 DFJ-35 DFJ-40 DFJ-45 DFJ-50 DFJ-60

DFJ-70 DFJ-80 DFJ-90 DFJ-100 DFJ-110 DFJ-125 DFJ-150 DFJ-175 DFJ-200

DFJ-225 DFJ-250 DFJ-300 DFJ-350 DFJ-400 DFJ-450 DFJ-500 DFJ-600

Data Sheet: 1048

For product data sheets, visit www.cooperbussmann.com/datasheets/ulcsa

97

High Speed Fuses

North American — FWA 130V: 1000-4000A Arc Voltage

FWA

This curve gives the peak arc voltage, UL, which may appear across the fuse during its operation as a function of the applied working voltage, Eg, (rms) at a power factor of 15%.

Specifications Description: North American style flush-end high speed fuses. Dimensions: See Dimensions illustrations. Ratings: Volts: — 130Vac Amps: — 1000-4000A IR: — 200kA RMS Sym. — 50kA @130Vdc Agency Information: CE, UL Recognized on 1000-2000A fuses

Watts loss at rated current is given in the electrical characteristics. The curve allows the calculation of the power losses at load currents lower than the rated current. The correction factor, Kp, is given as a function of the RMS load current, Ib, in % of the rated current.

I2t

The total clearing I2t at rated voltage and at power factor of 15% are given in the electrical characteristics. For other voltages, the clearing I2t is found by multiplying by correction factor, K, given as a function of applied working voltage, Eg, (rms).

1.5 K 1.0

200

100 Eg 50

0.5

0.6 0.5 0.4 0.3 0.2

Ib

0.1

0.3 0.2

Catalog Numbers FWA-1000AH FWA-1200AH FWA-1500AH FWA-2000AH FWA-2500AH FWA-3000AH FWA-4000AH

Eg

0.15 26

B 2.0 3.0 3.5

C 1.0 1.5 1.5

65

D — — 1.5

Fig. 1: 1000-3000A

104

130

Thread Depth Tapped 3⁄8”-24 x 1⁄2” Tapped 1⁄2”-20 x 1⁄2” Tapped 1⁄2”-20 x 1⁄2”

Fig. 2: 4000A

1.875

1.875

70

Electrical Characteristics I2t (A2 Sec) Rated Current Clearing RMS-Amps Pre-arc at 130V 1000 170000 460000 1200 270000 730000 1500 520000 1400000 2000 860000 2400000 2500 1500000 4100000 3000 2100000 5700000 4000 3400000 9200000

• • • •

Features and Benefits Excellent DC performance Low arc voltage and low energy let-through (I2t) Low watts loss Superior cycling capability

• • • •

Typical Applications DC common bus DC drives Power converters/rectifiers Reduced voltage starters

D

C

B

C

Data Sheet: 720001

98

60

• Watts loss provided at rated current. • See accessories on page 113.

Fig. 1 1 2

150

80 90 100%

Catalog Numbers

1mm = 0.0394˝ / 1˝ = 25.4mm

B

100

1.0 Kp 0.8

30 40 50

Dimensions (in) Catalog Number FWA-1000AH-2000AH FWA-2500AH-3000AH FWA-4000AH

300

Power Losses

Electrical Characteristics Total Clearing

UL

For product data sheets, visit www.cooperbussmann.com/datasheets/ulcsa

Watts Loss 60 70 78 108 130 150 257

High Speed Fuses

North American — FWA 130V: 1000-4000A FWA 1000-4000A: 130V Time-Current Curve 104 6 4 2 103 6 4

FWA-1000AH FWA-1200AH FWA-1500AH FWA-2000AH FWA-2500AH FWA-3000AH FWA-4000AH

2 102 6 4

High Speed Fuses

Virtual Pre-Arcing Time In Seconds

2 101 6 4 2 10

0

6 4 2 10–1 6 4 2 10–2 6 4 2 10–3 6 4 2 10–4

2

103

4

6 8 2 4 104 Prospective Current In Amps RMS

6

8

105

Peak Let-Through Curve 2

105

6

Peak Let-Through Current

4

2 FWA-4000AH FWA-3000AH 104

FWA-2500AH FWA-2000AH FWA-1500AH

6

FWA-1200AH FWA-1000AH

4

2

103 103

2

4

6

104

2

4

6

105

Prospective Short-Circuit Current Symmetrical RMS

2

4

6

Data Sheet: 35785301

For product data sheets, visit www.cooperbussmann.com/datasheets/ulcsa

99

High Speed Fuses

North American — FWA 150V: 70-1000A FWA

Arc Voltage This curve gives the peak arc voltage, UL, which may appear across the fuse during its operation as a function of the applied working voltage, Eg, (rms) at a power factor of 15%.

Specifications Description: North American style stud-mount fuses. Dimensions: See Dimensions illustrations. Ratings: Volts: — 150Vac/dc Amps: — 70-1000A IR: — 100kA Sym. (70-400A) — 200kA Sym. (450-1000A) — 20kA @150Vdc (70-800A) — 100kA @ 80Vdc (70-400A) Agency Information: CE, UL Recognized

K

1.0

50

0.5 0.3 0.2 0.15 22

1)

2)

Eg

70

102

150

2.656 2.188

Catalog Number FWA-70B FWA-80B FWA-100B FWA-125B FWA-150B FWA-200B FWA-250B FWA-300B FWA-350B FWA-400B FWA-500A FWA-600A FWA-700A FWA-800A FWA-1000A

Rated Current RMS-Amps 70 80 100 125 150 200 250 300 350 400 500 600 700 800 1000

0.125

1.000

0.438

0.4 0.3 0.2

Ib

0.1 60

70

Electrical Characteristics I2t (A2 Sec) Clearing Pre-arc at 150V 470 4000 670 6000 1200 12000 1870 18000 2700 26000 4780 45000 7470 70000 10760 100000 15700 140000 20300 180000 39000 120000 46000 140000 75000 220000 92000 280000 170000 510000

80 90 100%

Watts Loss 6.9 7.7 9.0 11.2 13.5 17.6 22.5 27.0 30.6 35.2 35.0 47.0 49.0 58.0 60.0

• • • •

Features and Benefits Excellent DC performance Low arc voltage and low energy let-through (I2t) Low watts loss Superior cycling capability

• • • •

Typical Applications DC common bus DC drives Power converters/rectifiers Reduced voltage starters

Fig. 2: 500-1000A 3.500 2.438 1.250

0.250

150

0.6 0.5

• Watts loss provided at rated current. • See accessories on page 113.

1.936 1.156

1.500

0.406 1mm = 0.0394” / 1” = 25.4mm

Data Sheet: 720002

100

100

1.0 Kp 0.8

Catalog Numbers

Dimensions (in) Fig. 1: 70-400A

1.000

100

30 40 50

1) 500-1000A Range 2) 70-400A Range

0.750 0.312

200

Eg

Watts loss at rated current is given in the electrical characteristics. The curve allows the calculation of the power losses at load currents lower than the rated current. The correction factor, Kp, is given as a function of the RMS load current, Ib, in % of the rated current.

1.5

The total clearing I2t at rated voltage and at power factor of 15% are given in the electrical characteristics. For other voltages, the clearing I2t is found by multiplying by correction factor, K, given as a function of applied working voltage, Eg, (rms).

300

Power Losses

Electrical Characteristics Total Clearing I2t

UL

For product data sheets, visit www.cooperbussmann.com/datasheets/ulcsa

High Speed Fuses

North American — FWA 150V: 70-1000A FWA 70-1000A: 150V Time-Current Curve 104 6 4 2 103 6 4

FWA-500A FWA-600A FWA-700A FWA-800A FWA-1000A

2 102 6 4

10

High Speed Fuses

Virtual Pre-Arcing Time In Seconds

2 1

6 4 2 100 6 4 2 10–1 6 4

FWA-70A FWA-80A FWA-100A FWA-125A FWA-150A

2 10–2 6 4 2 –3

10

FWA-200A FWA-250A FWA-300A FWA-350A FWA-400A

6 4 2 10–4

2

102

4

6 8 2 4 6 103 Prospective Current In Amps RMS

8

104

Peak Let-Through Curve 106

6 4

FWA-400A FWA-350A 2

FWA-300A FWA-250A

104

FWA-200A

Peak Let-Through Current

FWA-150A 6

FWA-100A

4

2

3

10

6

FWA-80A

4

FWA-70A

2

102 2 102

4

6

2 103

4

6

2 104

4

6

2 105

Prospective Short-Circuit Current Symmetrical RMS

Data Sheet: 35785310

For product data sheets, visit www.cooperbussmann.com/datasheets/ulcsa

101

High Speed Fuses

North American — FWX 250V: 35-2500A FWX

Arc Voltage This curve gives the peak arc voltage, UL, which may appear across the fuse during its operation as a function of the applied working voltage, Eg, (rms) at a power factor of 15%.

Specifications Description: North American style stud-mount and flush-end fuses. Dimensions: See Dimensions illustrations. Ratings: Volts: — 250Vac/dc Amps: — 35-2500A IR: — 200kA RMS Sym. Agency Information: CE, UL Recognized & CSA Component Acceptance on 35-800A fuses (20kA IR @250Vdc).

Power Losses Watts loss at rated current is given in the electrical char acteristics. The curve allows the calculation of the power losses at load currents lower than the rated current . The correction factor, K p , is given as a function of the RMS load current, Ib , in % of the rated current .

1.5

Electrical Characteristics

K 1.0

Total Clearing I t 2

The total clearing I2t at rated voltage and at power factor of 15% are given in the electrical characteristics. For other voltages, the clearing I2t is found by multiplying by correction factor, K, given as a function of applied working voltage, Eg, (rms).

0.5

1)

0.3 0.2 Eg

0.15

Fig. 1: 35-800A

D 2.59 2.44 2.94 3.03 — 1.50

75

125

200

250

300

1) 35-800A Range 2) 1000-2500A Range

E 2.25 2.19 2.25 2.28 — —

F 0.34 0.34 0.41 0.41 — —

G 0.63 1.00 1.00 1.50 — —

Fig. 2: 1000-1200A

H 0.13 0.19 0.25 0.25 — —

J 0.52 0.47 0.75 0.78 — —

Tapped Thread Depth — — — — 3 ⁄8”-24 x 1⁄2” 3 ⁄8”--24 x 1⁄2”

Fig. 3: 1500-2500A

J A A

A D E C

D

B

F G

800 600 500 400

Catalog Number FWX-35A FWX-40A FWX-45A FWX-50A FWX-60A FWX-70A FWX-80A FWX-90A FWX-100A FWX-125A FWX-150A FWX-175A FWX-200A FWX-225A FWX-250A FWX-275A FWX-300A FWX-350A FWX-400A FWX-450A FWX-500A FWX-600A FWX-700A FWX-800A FWX-1000AH FWX-1200AH FWX-1500AH FWX-1600AH FWX-2000AH FWX-2500AH

Rated Current RMS-Amps 35 40 45 50 60 70 80 90 100 125 150 175 200 225 250 275 300 350 400 450 500 600 700 800 1000 1200 1500 1600 2000 2500

C

C

102

2) Eg

200 50

100

150

200

250

1) 35-800A Range 2) 1000-2500A Range

1.0 Kp 0.8 0.6 0.5 0.4 0.3 0.2

Ib

0.1 60

Electrical Characteristics I2t (A2 Sec) Clearing Pre-arc at 250V 50 230 60 310 80 390 100 520 140 740 330 1400 430 1850 570 2450 740 3150 1130 4850 1620 6950 2170 9300 2790 12000 3210 14700 3960 18100 4720 21600 6000 27300 10600 48600 14500 66100 22100 101000 28000 128000 41100 188000 48800 190000 59000 230000 44000 360000 92000 750000 120000 880000 160000 1200000 320000 2300000 670000 4700000

70

80 90 100%

Watts Loss 4.2 5.2 5.7 6.0 8.1 7.2 8.1 9.0 10.0 12.5 15.7 18.5 22 24 27 31 32 39 44 49 54 62 72 84 100 103 140 140 151 163

• See accessories on page 113.

Features and Benefits • Excellent DC performance • Low arc voltage and low energy let-through (I2t) • Superior cycling capability

• • • •

Typical Applications DC common bus DC drives Power converters/rectifiers Reduced voltage starters

H

B

1)

300

30 40 50

• Watts loss provided at rated current. B

UL

103

Catalog Numbers 2)

Dimensions (in) Amp Rang e Fig. A B C 35-60 1 3.19 0.81 1.59 70-200 1 3.13 1.22 1.59 225-600 1 3.84 1.50 1.59 700-800 1 3.84 2.00 1.59 1000-1200 2 2.59 3.00 1.50 1500-2500 3 2.59 3.50 1.50 1mm = 0.0394” / 1” = 25.4mm

1.4 1.2

Data Sheet: 720005

For product data sheets, visit www.cooperbussmann.com/datasheets/ulcsa

High Speed Fuses

North American — FWX 250V: 35-2500A FWX 35-800A: 250V

FWX 1000-2500A(H): 250V

Time-Current Curve

Time-Current Curve 104 6 4

104

2

103

3

10 FWX-200A FWX-350A FXW-400A FWX-500A FWX-600A FWX-800A

6 4 2

FWX-1000AH FWX-1200AH FWX-1500AH FWX-1600AH FWX-2000AH FWX-2500AH

2

10

101

6 4 2 Virtual Pre-Arcing Time In Seconds

100

FWX-35A FWX-40A FWX-60A FWX-70A FWX-100A FWX-150A

10–1

10–2

10–3

10–4 102

2

103 Prospective Current In Amps RMS

104

1

High Speed Fuses

Virtual Pre-arcing Time In Seconds

102

10

6 4 2 100 6 4 2 10–1 6 4 2 10–2 6 4

Peak Let-Through Curve

2 105

10–3 6 4

B

2 FWX-800A FWX-600A FWX-400A FWX-300A FWX-200A

10–4

2

103

4

6 8 2 4 6 104 Prospective Current In Amps RMS

8

105

Peak Let-Through Current

104

Peak Let-Through Curve 105

6 FWX-2500AH 4

103

A

Peak Let-Through Current

FWX-150A FWX-100A FWX-70A FWX-60A FWX-45A FWX-35A

FWX-2000AH FWX-1600AH FWX-1500AH FWX-1200AH

2

FWX-1000AH

104

6 4

102

102

103

104

105

Prospective Short-Circuit Current Symmetrical RMS

2

103 103

2

4

6

104

2

4

6

105

2

4

6

Prospective Short-Circuit Current Symmetrical RMS

Data Sheet: 359

Data Sheet: 35785299

For product data sheets, visit www.cooperbussmann.com/datasheets/ulcsa

103

High Speed Fuses

North American — FWH 500V: 35-1600A FWH

Arc Voltage

2.0

Specifications Description: North American style stud-mount fuses. Dimensions: See Dimensions illustration. Ratings: Volts: — 500Vac/dc Amps: — 35-1600A IR: — 200kA Sym. — 50kA @ 500Vdc Agency Information: CE, UL Recognition & CSA Component Acceptance on 35-800A only (50kA [email protected]). UL Recognition on 35-1200A only, CSA Component Acceptance: 35-1600A.

This curve gives the peak arc voltage, UL, which may appear across the fuse during its operation as a function of the applied working voltage, Eg, (rms) at a power factor of 15%.

1.6

Electrical Characteristics Total Clearing I2t

1.5

The total clearing I2t at rated voltage and at power factor of 15% are given in the electrical characteristics. For other voltages, the clearing I2t is found by multiplying by correction factor, K, given as a function of applied working voltage, Eg, (rms).

1.0

K

0.5

2)

Fig. 1 1 1 1 1 1 1 2

Eg

0.15 100

250

400

500

1) 35-800A Range 2) 1000-1600A Range

Dimensions (in) Amp Rang e 35-60 70-100 125-200 225-400 450-600 700-800 1000-1200 1400-1600

A B 3.188 0.813 3.625 0.947 3.625 1.156 4.340 1.500 4.340 2.000 6.340 2.500 6.969 3.000 See Drawing

C 1.593 1.736 1.836 2.090 2.090 2.090 3.219

D 2.541 2.853 2.892 3.440 3.530 4.970 5.465

E 2.193 2.807 2.768 2.750 2.780 3.440 4.475

F 0.344 0.352 0.344 0.410 0.410 0.530 0.625

G 0.719 0.750 1.000 1.000 1.500 2.000 2.375

H 0.125 0.125 0.188 0.250 0.250 0.380 0.438

1mm = 0.0394” / 1” = 25.4mm

Fig. 1: 35-1200A A D E C

H

G F

B J

Fig. 2: 1400-1600A

10.219

0.125

0.5

3.219

0.625

3.5

104

103

800 600 2) 500 1)

400 300 100

Power Losses

Eg 200

300

400

500

1) 35-200 & 1000-1600A Range 2) 225-800A Range

Watts loss at rated current is given in the electrical characteristics. The curve allows the calculation of the power losses at load currents lower than the rated current. The correction factor, Kp, is given as a function of the RMS load current, Ib, in % of the rated current.

J 0.518 0.375 0.406 0.750 0.780 1.300 1.120

Catalog Numbers FWH-35B FWH-40B FWH-45B FWH-50B FWH-60B FWH-70B FWH-80B FWH-90B FWH-100B FWH-125B FWH-150B FWH-175B FWH-200B FWH-225A FWH-250A FWH-275A FWH-300A FWH-325A FWH-350A FWH-400A FWH-450A FWH-500A FWH-600A FWH-700A FWH-800A FWH-1000A FWH-1200A FWH-1400A FWH-1600A

Rated Current RMS-Amps 35 40 45 50 60 70 80 90 100 125 150 175 200 225 250 275 300 325 350 400 450 500 600 700 800 1000 1200 1400 1600

1.0 Kp 0.8 0.6 0.5 0.4 0.3 0.2

Ib

0.1 30 40 50

60

Electrical Characteristics I2t (A2 Sec) Clearing Pre-arc at 500V 34 150 76 320 105 450 135 670 210 900 210 900 305 1400 360 1600 475 2000 800 3500 1100 4600 1450 6200 1900 8500 4600 23300 6300 32200 7900 40300 9800 49800 13700 63800 14500 72900 19200 96700 24700 127000 29200 149000 41300 206000 55000 298000 76200 409000 92000 450000 122000 600000 200000 1000000 290000 1400000

• Watts loss provided at rated current.

1.625 1.750

6.219 8.969

1.2

70

80 90 100%

Catalog Numbers

1) 0.3 0.2

UL

0.75 4.25

Watts Loss 8 7.5 7.5 7.5 9.9 10.6 12.7 15 17 25 30 35 40 39 41 46 51 53 58 65 74 84 108 120 129 145 180 210 230

• See accessories on page 113.

Features and Benefits • Excellent DC performance • Low arc voltage and low energy let-through (I2t) • Superior cycling capability

• • • •

Data Sheet: 720007

For product data sheets, visit www.cooperbussmann.com/datasheets/ulcsa

Typical Applications DC common bus DC drives Power converters/rectifiers Reduced voltage starters

High Speed Fuses

North American — FWH 500V: 35-1600A FWH 35-200A(B) & 900-1600A(A): 500V Time-Current Curve 10

FWH 250-800A: 500V Time-Current Curve 103

4

6 4 2 103 6 4

102 FWH-300A FWH-400A FWH-500A FWH-600A FWH-800A

2 102 6 4

101

Virtual Pre-Arcing Time In Seconds

101 6 4 2 100 6 4

FWH-80B FWH-90B FWH-100B FWH-125B FWH-150B FWH-175B FWH-200B

FWH-35B FWH-40B FWH-45B FWH-50B FWH-60B FWH-70B

2 10–1 6 4 2 10–2 6 4

High Speed Fuses

FWH-900A FWH-1000A FWH-1200A FWH-1400A FWH-1600A

2

100

10–1

10–2

2 10–3 6 4

10–3

2 10–4

2

4

6

8

102

2 4 6 8 2 103 Prospective Current In Amps RMS

4

6

8

104

10–4 102

Peak Let-Through Curve

103 104 Prospective Current In Amps RMS

105

Peak Let-Through Curve

105

105

B

FWH-1600A FWH-1400A

6

FWH-1200A FWH-1000A

4

2

4

104 Peak Let-Through Current

Peak Let-Through Current

10

6 4

2

103

FWH-800A FWH-600A FWH-500A FWH-400A FWH-300A FWH-250A

103 FWH-200B 6

FWH-150B FWH-125B

4

A

FWH-100B FWH-80B FWH-60B FWH-50B

2

FWH-40B FWH-35B

102

102 102

2

4

6

103

2

4

6

104

2

4

6

105

2

102

103 104 Prospective Short-Circuit Current Symmetrical RMS

105

Prospective Short-Circuit Current Symmetrical RMS

Data Sheet: 35785304

Data Sheet: 360

For product data sheets, visit www.cooperbussmann.com/datasheets/ulcsa

105

High Speed Fuses

North American — KAC 600V: 1-1000A KAC

Catalog Numbers (Amps) KAC-1 KAC-2 KAC-3 KAC-4 KAC-5 KAC-6 KAC-7 KAC-8 KAC-9 KAC-10 KAC-12 KAC-15 KAC-17.5 KAC-20

Specifications Description: North American style stud-mount fuses. These 600V fuses are supplied as replacements only. For new installations, Cooper Bussmann recommends the 700V FWP Series fuse. Dimensions: See Dimensions illustrations. Ratings: Volts: — 600Vac Amps: — 1-1000A IR: — 200kA RMS Sym. Agency Information: CE, UL Recognition on 1-600A only.

KAC-25 KAC-30 KAC-35 KAC-40 KAC-45 KAC-50 KAC-60 KAC-70 KAC-80 KAC-90 KAC-100 KAC-110 KAC-125 KAC-150

KAC-175 KAC-200 KAC-225 KAC-250 KAC-300 KAC-350 KAC-400 KAC-450 KAC-500 KAC-600 KAC-700 KAC-800 KAC-1000

• See accessories on page 113.

Features and Benefits • Low arc voltage and low energy let-through (I2t) • Low watts loss • Superior cycling capability Typical Applications • Power converters/rectifiers • Reduced voltage starters

Dimensions (in) Amp Rang e 1-30A 35-60A 70-100A 110-200A 225-400A 450-800A 1000A

Fig. 1 2 2 2 2 1 1

A 2.875 4.375 5.000 5.140 6.182 6.250 7.250

B1 2.500 – – – – 4.750 4.750

B2 – 3.750 4.063 4.390 4.815 – –

B3 – 3.500 3.656 3.766 4.565 – –

C 1.875 2.750 2.750 2.906 3.000 3.063 3.063

D 0.406 0.625 0.750 1.000 1.625 2.000 2.750

E – 0.343 0.406 0.406 0.562 – –

F 0.563 0.813 1.000 1.500 2.000 2.500 3.500

G 0.063 0.094 0.125 0.188 0.250 0.250 0.375

H 0.257 0.468 0.609 0.718 0.687 0.563 0.563

1mm = 0.0394˝ / 1˝ = 25.4mm

Fig. 1: 1-30 & 450-1000A A B1 C

G

D

F

H

Fig. 2: 35-400A A B2 B3 C

D

G

F

E

H

Data Sheet: 720009

106

For product data sheets, visit www.cooperbussmann.com/datasheets/ulcsa

High Speed Fuses

North American — KBC 600V: 35-800A KBC

Catalog Numbers (Amps) KBC-100 KBC-110 KBC-125 KBC-150 KBC-175 KBC-200 KBC-225 KBC-250

KBC-300 KBC-350 KBC-400 KBC-450 KBC-500 KBC-600 KBC-800

• See accessories on page 113.

Features and Benefits • Low arc voltage and low energy let-through (I2t) • Low watts loss • Superior cycling capability Typical Applications • Power converters/rectifiers • Reduced voltage starters

High Speed Fuses

Specifications Description: North American style stud-mount and flush-end fuses. These 600V fuses are supplied as replacements only. For new installations, Cooper Bussmann recommends the 700V FWP Series fuse. Dimensions: See Dimensions illustrations. Ratings: Volts: — 600Vac Amps: — 35-800A IR: — 200kA RMS Sym. Agency Information: CE, UL Recognition on 35-600A only.

KBC-35 KBC-40 KBC-45 KBC-50 KBC-60 KBC-70 KBC-80 KBC-90

Dimensions (in) Amp Rang e 35-60A 70-100A 110-200A 225-400A 450-600A 800A

Fig. 1 2 1 1 1 3

A B C 4.375 3.750 3.500 See Drawing 4.406 3.719 3.594 5.125 4.188 3.563 5.125 4.389 3.687 See Drawing

D E F G H I 2.750 0.343 0.625 0.813 0.094 0.468 2.906 0.312 0.875 1.219 0.187 0.375 2.906 0.406 1.000 1.500 0.250 0.719 2.875 0.406 1.500 2.000 0.250 0.757

1mm = 0.0394” / 1” = 25.4mm

Fig. 1: 35-60 and 110-600A A B C D

E

H

F

G

I

0.312

0.750

1.000

0.125

4.406

3.656

2.906

Fig. 2: 70-100A

Fig. 3: 800A 4.000 3.750

‹/•" - 24 ≈ ⁄/™" 0.750

2.500 2.859

0.750

Data Sheet: 720010

For product data sheets, visit www.cooperbussmann.com/datasheets/ulcsa

107

High Speed Fuses

North American — FWP 700V: 5-1200A FWP Specifications Description: North American style stud-mount fuses. Dimensions: See Dimensions illustrations. Ratings: Volts: — 700Vac/dc Amps: — 5-1200A IR: — 200kA RMS Sym. — 50kA @700Vdc Agency Information: CE, UL Recognition & CSA Component Acceptance on 5-800A

The total clearing I t at rated voltage and at power factor of 15% are given in the electrical characteristics. For other voltages, the clearing I2t is found by multiplying by correction factor, K, given as a function of applied working voltage, Eg, (rms).

K 1.0 2)

C 1.855 2.750 2.594 2.840 2.840 2.840 2.844

1) 0.3 0.2

3) Eg

0.15 316

460

604

700

E 2.477 3.312 3.563 3.500 3.530 4.190 5.062

F 0.250 0.344 0.344 0.410 0.410 0.530 0.625

G 0.405 0.725 0.750 1.000 1.500 2.000 1.500

H 0.063 0.125 0.125 0.250 0.250 0.380 0.250

I 0.250 0.542 0.375 0.750 0.780 1.300 0.875

1mm = 0.0394” / 1” = 25.4mm

Fig. 1: 5-800A

Fig. 2: 900-1000A

Fig. 3: 1200A 3.500

1.375 0.125

J

0.500

5.966 7.594

A D E C

9.590 6.840

3.844

0.625

1.031

2.750 0.5 3.500 H B

6 5 Eg 300

500

600

0.750 4.250

Catalog Numbers FWP-5B FWP-10B FWP-15B FWP-20B FWP-25B FWP-30B FWP-35B FWP-40B FWP-50B FWP-60B FWP-70B FWP-80B FWP-90B FWP-100B FWP-125A FWP-150A FWP-175A FWP-200A FWP-225A FWP-250A FWP-300A FWP-350A FWP-400A FWP-450A FWP-500A FWP-600A FWP-700A FWP-800A FWP-900A FWP-1000A FWP-1200A

Rated Current RMS-Amps 5 10 15 20 25 30 35 40 50 60 70 80 90 100 125 150 175 200 225 250 300 350 400 450 500 600 700 800 900 1000 1200

700

1) 125-600A Range 2) 35-100 & 700-1200A Range

1.0 Kp 0.8 0.6 0.5 0.4 0.3 0.2

Ib 30 40 50

60

Electrical Characteristics I2t (A2 Sec) Clearing Pre-arc at 700V 1.6 10 3.6 20 10 75 26 180 44 340 58 450 34 160 76 320 135 600 210 950 305 2000 360 2400 415 2700 540 3500 1800 7300 2900 11700 4200 16700 5500 22000 7700 31300 10500 42500 17600 71200 23700 95600 31000 125000 36400 137000 45200 170000 66700 250000 54000 300000 78000 450000 91500 530000 120000 600000 195000 1100000

Features and Benefits • Excellent DC performance • Low arc voltage and low energy let-through (I2t) • Superior cycling capability

• • • •

70

80 90 100%

Watts Loss 1.5 4 5.5 6 7 9 12 12 12 15.5 18 21 25 27 28 32 35 43 45 48 58 65 78 94 107 122 125 140 150 170 190

Typical Applications DC common bus DC drives Power converters/rectifiers Reduced voltage starters

Data Sheet: 720012

108

400

• Watts loss provided at rated current. • See accessories on page 113.

1.625 1.750

0.625

G

3.844 10.844

5.154

F

2)

8

Catalog Numbers

0.5

D 2.477 3.708 3.625 4.190 4.280 5.720 5.562

1)

0.1

Dimensions (in) A B 2.870 0.563 4.375 0.813 4.406 0.947 5.090 1.500 5.090 2.000 7.090 2.500 6.630 2.000 See Drawing See Drawing

UL

3

Watts loss at rated current is given in the electrical characteristics. The curve allows the calculation of the power losses at load currents lower than the rated current. The correction factor, Kp, is given as a function of the RMS load current, Ib, in % of the rated current.

1) 35-100A Range 2) 125-600A Range 3) 700-1200A Range

Amp Rang e Fig. 5-30 1 35-60 1 70-100 1 125-200 1 225-400 1 450-600 1 700-800 1 900-1000 2 1200 3

1.6 1.4 1.2 103

4

1.5

2

2

This curve gives the peak arc voltage, UL, which may appear across the fuse during its operation as a function of the applied working voltage, Eg, (rms) at a power factor of 15%. Power Losses

Electrical Characteristics Total Clearing I2t

Arc Voltage

For product data sheets, visit www.cooperbussmann.com/datasheets/ulcsa

High Speed Fuses

North American — FWP 700V: 5-1200A FWP 5-30A(B): 700V

FWP 35-100A(B) & 700-1200A(A): 700V

Time-Current Curve

Time-Current Curve 104

104 6 4

6 4

2

2 103

103

6 4

6 4

2

2

6 4

6 4

2 Virtual Pre-Arcing Time In Seconds

6 4 2 100 6 4

FWP-5B FWP-10B FWP-15B FWP-20B FWP-25B FWP-30B

2 10–1 6 4

101 6 4

FWP-35B FWP-40B FWP-50B FWP-60B FWP-70B FWP-80B FWP-90B FWP-100B

2 100 6 4

High Speed Fuses

Virtual Pre-Arcing Time In Seconds

2 101

2 10–1 6 4 2

2 10–2

10–2

6 4

6 4

2

2 10–3

10–3

6 4

6 4

2

2 10–4

FWP-700A FWP-800A FWP-900A FWP-1000A FWP-1200A

102

102

10–4 2

4

6

8

2

101

4

6

8

2

102

4

6

8

103

2

4

6

8

2 4 6 8 2 103 Prospective Current In Amps RMS

102

Prospective Current In Amps RMS

Peak Let-Through Curve

4

6

8

104

Peak Let-Through Curve 106

104

FWP-1200A

6

FWP-1000A

6

FWP-800A

4

4

FWP-700A

2 FWP-30B FWP-25B

2

104

6 4

Peak Let-Through Current

Peak Let-Through Current

10

3

2

10

FWP-20B FWP-15B FWP-10B FWP- 5B

2

6 4

6 4

2

103

2

6 FWP-100B 4

101 101

2

4

6

102

2

4

6

103

2

4

6

104

2

4

6

105

FWP-70B

2

FWP-60B

Prospective Short-Circuit Current

FWP-50B

2

FWP-40B FWP-35B 102 2

4

6

102

2

4

6

103

2 104

4

2

6 105

Prospective Short-Circuit Current

Data Sheet: 35785316

Data Sheet: 35785308

For product data sheets, visit www.cooperbussmann.com/datasheets/ulcsa

109

High Speed Fuses

North American — FWP 700V: 5-1200A FWP 150-600A: 700V Time-Current Curve 103

102

FWP-150A FWP-200A FWP-300A FWP-400A FWP-600A

Virtual Pre-Arcing Time In Seconds

101

100

10–1

10–2

10–3

10–4 102

103

104

105

Prospective RMS ProspectiveCurrent CurrentInInAmperes Amps RMS

Peak Let-Through Curve

105

B

Peak Let-Through Current

104

FWP-600A FWP-400A FWP-300A FWP-200A FWP-150A 103

A

102

102

103

104

105

Prospective Short-Circuit Current Symmetrical RMS

Data Sheet: 361

110

For product data sheets, visit www.cooperbussmann.com/datasheets/ulcsa

High Speed Fuses

North American — FWJ 1000V: 35-2000A FWJ

Arc Voltage

Specifications Description: North American style stud-mount fuses. Dimensions: See Dimensions illustration. Ratings: Volts: — 1000Vac Amps: — 35-2000A IR: — 25kA (35-200A) — 100kA (250-2000A) — 50kA @ 800Vdc (35200A, 450-600A) Agency Information: CE, UL Recognition File E91958 on 35-600A only.

C 3.110 3.085 3.261 3.500 3.465 3.312

K

1000 1400 1800

Ib 60

70

80 90 100%

Catalog Numbers

0.5 0.3 0.2 Eg

0.15 200

500

800

1000

E 4.180 4.156 4.055 4.150 4.706 4.962

F 0.352 0.352 0.445 0.433 0.562 0.625

G 0.750 1.000 1.000 1.500 2.000 2.750

H 0.125 0.188 0.250 0.250 0.375 0.500

I 0.380 0.407 0.819 0.764 1.201 0.880

1mm = 0.0394” / 1” = 25.4mm

Fig. 1: 35-2000A A D E C

H

G F

B J

Data Sheet: 720027

600

Kp

30 40 50

1.0

D 4.235 4.266 4.803 4.811 5.984 5.472

400

High Speed Fuses

B 0.940 1.125 1.526 2.000 2.500 3.500

800

Eg

Watts loss at rated current is 1.0 given in the electrical characteristics. The curve 0.8 allows the calculation of the 0.6 0.5 power losses at load 0.4 currents lower than the 0.3 rated current. The correction factor, Kp, is 0.2 given as a function of the RMS load current, Ib, in % of the rated current. 0.1

Dimensions (in) Amp Rang e Fig. A 35-60 1 5.000 70-100 1 4.932 125-200 1 5.685 250-400 1 5.768 500-600 1 7.201 800-2000 1 6.811

1200

200

1.5

The total clearing I2t at rated voltage and at power factor of 15% are given in the electrical characteristics. For other voltages, the clearing I2t is found by multiplying by correction factor, K, given as a function of applied working voltage, Eg, (rms).

UL 1600

Power Losses

Electrical Characteristics Total Clearing I2t

2000

This curve gives the peak arc voltage, UL, which may appear across the fuse during its operation as a function of the applied working voltage, Eg, (rms) at a power factor of 15%.

Catalog Numbers FWJ-35A FWJ-40A FWJ-50A FWJ-60A FWJ-70A FWJ-80A FWJ-90A FWJ-100A FWJ-125A FWJ-150A FWJ-175A FWJ-200A FWJ-250A FWJ-300A FWJ-350A FWJ-400A FWJ-500A FWJ-600A FWJ-800A FWJ-1000A FWJ-1200A FWJ-1400A FWJ-1600A FWJ-1800A FWJ-2000A

Rated Current RMS-Amps 35 40 50 60 70 80 90 100 125 150 175 200 250 300 350 400 500 600 800 1000 1200 1400 1600 1800 2000

Electrical Characteristics I2t (A2 Sec) Clearing Pre-arc at 1000V 210 2000 300 2500 470 3500 670 5000 1100 6900 1550 9700 1900 12000 2800 17500 4800 35000 6300 45000 7500 65000 11700 80000 16000 112000 23500 164000 33000 231000 47000 330000 39500 329000 61000 520000 87000 500000 190000 1100000 370000 2100000 470000 2700000 700000 4000000 925000 5300000 1330000 7600000

Watts Loss 7 8 10 11 12 13 14 15 16 25 30 32 50 56 62 67 95 105 182 206 240 248 267 239 244

• Watts loss provided at rated current. • See accessories on page 113.

• • • •

Features and Benefits Excellent DC performance Low arc voltage and low energy let-through (I2t) Low watts loss Superior cycling capability

• • • •

Typical Applications DC common bus DC drives Power converters/rectifiers Reduced voltage starters

For product data sheets, visit www.cooperbussmann.com/datasheets/ulcsa

111

High Speed Fuses

North American — FWJ 1000V: 35-2000A FWJ 35-600A: 1000V

FWJ 800-2000A: 1000V

Time-Current Curve

Time-Current Curve

104

104

6 4

6 4

2

2 103

103

6 4

6 4

2

2 102

102

101 6 4

Virtual Pre-Arcing Time In Seconds

2 Virtual Pre-Arcing Time In Seconds

6 4

FWJ-200A FWJ-250A FWJ-300A FWJ-350A FWJ-400A FWJ-500A FWJ-600A

6 4

2 100 6 4 2

101 6 4 2 100 6 4 2 10–1 6 4

10–1 6 4 2 10–2 6 4 2 10–3

FWJ-800A FWJ-1000A FWJ-1200A FWJ-1400A FWJ-1600A FWJ-1800A FWJ-2000A

2

FWJ-40A FWJ-50A FWJ-60A FWJ-70A FWJ-80A FWJ-90A FWJ-100A FWJ-125A FWJ-150A FWJ-175A

2 10–2 6 4 2 10–3 6 4

6 4

2 10–4

2 10–4 102

2

4

6

8

2

103

4

6

8

2

4

6

8

2

103

4

6

8

104

Prospective Current In Amps RMS

Data Sheet: 35785309

Peak Let-Through Curve 2 FWJ-2000A FWJ-1800A FWJ-1600A FWJ-1400A FWJ-1250A FWJ-1000A FWJ-600A FWJ-800A FWJ-400A FWJ-500A FWJ-350A FWJ-300A FWJ-250A FWJ-200A FWJ-175A FWJ-150A FWJ-125A FWJ-100A FWJ-90A FWJ-80A FWJ-70A FWJ-60A FWJ-50A FWJ-40A

105 6 4

Peak Let-Through Current

2

104 6 4

2

103 6 4

2

102 102

2

4

6

2

103

4

6

104

2

4

6

105

2

4

6

Prospective Short-Circuit Current Symmetrical RMS

Data Sheet: 35785303

112

104

2

Prospective Current In Amperes Prospective Current in AmpsRMS

For product data sheets, visit www.cooperbussmann.com/datasheets/ulcsa

4

6

8

105

High Speed Fuses

North American Fuse Accessories Fuse Bases (Blocks) Modular Style Cooper Bussmann offers a comprehensive line of fuse bases that provide the user with design and manufacturing flexibility. Two identical half bases make up a Cooper Bussmann® modular fuse base. These “split” units can be panel mounted any distance apart to accommodate any length fuse. Stud Type (Not sold in pairs)

C5268 Series

Stud Type

Connector Type

High Speed Fuses

The simpler design is the C5268 Series modular fuse base. With this design, the fuse terminal and cable (with termination) are mounted on the same stud, minimizing labor needed for installation. The stud type base is available in the configuration shown in the table below. Catalog Max Fuse Stud Stud Dia. Number Amp Rating Height (in) & Threads 5 C5268-1 200 1.00 ⁄16˝-18 5 C5268-2 200 1.75 ⁄16˝-18 5 C5268-3 200 0.75 ⁄16˝-18 1 C5268-4 100 1.00 ⁄4˝-20 1 C5268-5 100 1.75 ⁄4˝-20 BS Style

Connector Type

Cooper Bussmann also offers a modular style fuse base that utilizes a tin-plated connector (for wire termination and heat dissipation) and a plated-steel stud (for fuse mounting). The connector type fuse base is available in the configurations shown below. Consult Cooper Bussmann for additional product details. Modular Max Max Fuse Data Sheet Base Style Voltage Amp Rating Number 1BS101 600 100 1206 1BS102 600 400 1207 1BS103 600 400 1208 1BS104 600 600 1209 BH-0xxx 700 100 1200 BH-1xxx 2500 400 1201 BH-2xxx 5000 400 1202 BH-3xxx 1250 700 1203 Refer to page 275 for BH style holders.

Fixed Center Fixed Center Base Style Cooper Bussmann offers a comprehensive line of fixed mount style fuse bases under the trademark TRON® rectifier fuse blocks. The cable and fuse connections are similar to the stud type fuse base — both are mounted on the same stud. Consult Cooper Bussmann for complete product details.

For product data sheets, visit www.cooperbussmann.com/datasheets/ulcsa

113

Recommend Documents
Dimensions â mm. Land Pattern. Electrical Characteristics. Rated. 1.5 xIn 2.1 xIn. 2.75 xIn. 4 xIn. 10 xIn. Current min max min max min max min max. 40mA-6.3A 1hr 2 min 400 mS10 Sec. 150 mS 3 Sec. 20 mS 150 mS. Subminiature Fuses. SR-5 Series, Time

Mar 11, 2002 - 1336Tâ _ _ 060. 45. 60. 250. 125. 90. 1336Tâ _ _ 075. 56. 75. â. 150. 110. 1336Tâ _ _ 100. 75. 100. â. 200. 150. 1336Tâ _ _ 125. 93. 125. â.

Blister Tri-Lingual. (Amps). Pack. Blister. FLM-30. X. FLM-60. X. X. FLM-80. X. X ... and High Amp Fuses & Fusible Links. No. Blister. (Amps). Pack. FLD-30. X.

additional center indicator in front for easy and quick identification of operated fuse ... Dual Indication Saves Time & Money by quicker identification,. Insulated ...

Medium. V oltage. Fuses. Section Contents. Page. Introduction ... worldwide distribution network with unrivaled service and technical support. Cooper Bussmann ...

SF or XL13X(Amp). RFA(Amp). SF13X(Amp) ... In many cases, the data in this catalog section which includes available ratings ... must not open. For permitted ...

Indicator System. 185. Fuse Bases. 186. Square Body Fuse Ranges. Amps. Volts. AC. DC .... Low arc voltage and low energy let-through (I2t). â¢ Low watts loss.

EEI-NEMA Type K & T and Type H & N fuses . . . 88. BBU Boric acid fuses . . . . . . . . . . . . . . . . . . . 89-90. Fuseclips for medium and high voltage fuses . . . 91 ... of 15 â 35sec at a current equal to 100 times the âRâ rating. Cooper B